Accessible Bathroom and WC in Dwellings
In this section of our Metric Data series we will look at accessible sanitary facilities. This refers to designing wheelchair accessible bathrooms and wheelchair accessible WCs.
You can download the PDF of this post by clicking on the button below.
You can also download the cad files for a small fee by following the link below:
The building regulations have varying requirements in terms of accessible sanitary facilities, according to the category you are working towards:
M4 (1) – Visitable Dwellings
M4 (2) – Accessible and adaptable dwellings
M4 (3) – Wheelchair user dwellings
Category M4 (1) is considered to be a compulsory requirement, and the other categories optional unless a condition is imposed on a new development as part of the process of granting planning permission. If no condition is imposed the dwelling will only need to meet requirements for M4 (1), but if the condition is imposed to M4 (2) or (3) it may be that specific dwellings in a development must comply.
My personal feeling is that all dwelling should be as accessible as possible, or at the very least as adaptable as possible. I think we should strive to do more than the bare minimum that our regulations set out and aim to achieve better accessibility and performance in our buildings regardless of government targets.
So for this reason, we will look at making the WC accessible and the bathroom accessible to wheelchair users, and work from section M4 (3) wheelchair user dwelling.
Be sure to always refer to the Building Regulations Approved Documents when designing accessible layouts and facilities.
Building Regulations Requirements for Accessible Bathrooms and WCs
General Provisions for accessible bathrooms and WCs
Any dwelling with four or more bed spaces must provide a minimum of two WCs in separate bathrooms or WC/cloakrooms.
Every room that contains a level access shower is constructed as a wet room.
Any walls, ducts and boxing in any sanitary facility must be strong enough to support grab rails, seats and other adaptations.
The ceiling structure must be strong enough to support an overhead hoist capable of carrying 200kg.
WC flush controls must be positioned in front of the cistern on the transfer side and can be easily gripped.
WC pans should be a minimum of 400mm high.
Basins and sinks should be wall hung, typically 770-850mm above floor level, with a clear zone beneath to allow wheelchair users to approach easily.
Accessible WC on the entrance storey
Sign up to our newsletter
Make sure you don’t miss out on anything that is going on at First In Architecture – sign up to the newsletter now. No spam, no funny business, just useful stuff!
Dwellings with up to four bedspaces should have a minimum of one bathroom containing a WC, basin and a level access shower, with the potential for a bath to be installed, (unless a bath is provided in addition to the shower, or in another bathroom on the same storey).
The WC, basin, shower and bath must have suitable clear access zones as shown in previous diagram.
Dwellings with five bed spaces or more must contain both a usable bath and a level access shower.
The level access shower must be positioned in a corner to enable a shower seat to be fitted on one wall with the shower controls on the adjacent wall.
The bathroom provides a minimum 1500mm clear turning circle.
Specifying underfloor heating allows the floor to dry faster
Safety glass for the shower screen can also have frosted manifestations
Ensure the bathroom door lock is operable from the outside
All walls should be constructed to be strong enough to take fittings and rails
Bath installations should include a transfer area at the end of the bath and ensure taps are fitted to be accessible to the nearest corner.
Don’t forget to download your PDF of this blog post, and get hold of the accompanying cad files too!